66kV 110kV 220kV HV Cable-
Single core,Copper conductor, XLPE insulation,Corrugated Aluminum sheath, or lead alloy sheath, or Copper wire Screen,PVC or PE Outer sheath power cable
1)The maximum rated working temperature of conductor is 90°C, and the maximum temperature is less than 250°C when short circuit occurs(no more than 5 seconds
2)Allowable maximum lateral pressure is 5KN/m.
3)Allowable maximum traction strength of aluminum conductor is 40N/mm2.
4)Cable laying temperature is not less than 0°C.
5)The minimum bending radius is no less than 20D.
(D---represents actual outer diameter of cable)5.Size range we produce:6.Packing:
3.Type and Application:
Wooden Drum, Steel Wooden Drum, All Steel Drum for very heavy cable